The WTR420 shall provide four levels of Radio Link Quality indication. The four levels shall be defined as HIGH, GOOD, LOW, and LOST. HIGH, shall indicate strong error free communication. GOOD, shall indicate good but less than ideal communication. LOW, shall indicate intermittent and unreliable communication. LOST, which shall indicate no communication with the Transmitter.
The WTR420 shall provide a BATTERY LOW indication to indicate the condition of the battery in the Transmitter. The indicator shall blink when the battery has low voltage and must be replaced.
The WTR420 shall contain Zero and Span potentiometers are for field calibration.
The WTR420 acts as a Modbus RTU slave. Connecting the RS-232 serial port (or optional Ethernet Port) to a SCADA system shall allow the liquid level to be monitored remotely.
Additional setup and troubleshooting features shall be available using the separately supplied Touch Screen Interface Device (TSID), manufactured by M.P. Electronics.
The Transmitter and Receiver shall be capable of reliable communication even with the Transmitter under the concrete slab of a lift station wet well. The Antenna for the Receiver shall be mounted external to the control panel that the Receiver is installed in. For applications where the Transmitter and Receiver Antenna have line of site, reliable communication shall be maintained at distances up to 125 feet.
The Wireless Transmitter shall be part number WTT-A-B, where A is the pressure range, and B is the cable length, The Wireless Receiver shall be part number WTR420-X, where X is blank for the standard unit with an RS232 Serial Port, or X equals E for the optional Ethernet connectivity.